|CBD-NET.com | Search | Subscribe to receive Updated Notices | Non-Print Version|
Document Type: PRESOL Posted Date: Jul 20, 2020 Category: Water Purification and Sewage Treatment Equipment Set Aside: N/A
FA5004 354 CONS PK EIELSON AFB AK 99702-2200 USA
Any greensand filter media material that is provided must meet performance requirements set by manufacturers technical manual (Hungerford & Terry, Inc.) and meet NSF-61 criteria for drinking water. All media must be a like-for-like for existing media. If not like-for like change-out, prior approval from ADEC drinking water engineering group would be required prior to loading and use of new material. The Hungerford and Terry loaded greensand is 215 CuFt of GreensandPlus (Eff. Size 0.3-0.35mm / UC<1.6) and loaded anthrocite is 200 CuFt Anthrocite (Eff. Size 0.6-0.8mm / UC<1.6) in each filter. The WTP has six parallel greensand filters. Other competitive greensand and/or anthrocite will need thorough testing by the vendor and approval through ADEC prior to loading and use.
POC Marta Burke, Phone: 9073773519, Chrissina Dural, Phone: 9073773855
Eielson AFB, AK 99702, USA
Link: SAM.gov Permalink